Residential HVAC Services In Venus, Texas
The Midlothian, Texas area is known for its scorching hot summers and mild winters but that does not mean your home should go without proper heating and cooling technology to keep the temerature just right. When it comes to residential HVAC systems, there are typically four main types to keep in mind when
What Is A Residential HVAC System?
Residential Hvac Systems can generally be divided into 4 types:
- Split Systems
- Hybrid Heat Split System
Split-system air conditioners come in two forms: mini-split and central systems. In both types, the inside-environment (evaporative) heat exchanger is separated by some distance from the outside-environment (condensing unit) heat exchanger.
Hybrid Heat Split Systems
Common in U.S. homes and businesses, both in the U.S. and abroad. In these, an air handler that may contain a fan coil unit, a mechanism to heat the air and filter is placed inside a house or building and is connected to a condensing unit, which is outdoors. The air handler is controlled by a thermostat placed some distance away from the air handler. A user sets a desired temperature on the thermostat and the thermostat controls the air handler to maintain the set temperature. The air is fed through the air handler and, using ducts, into the spaces to be air conditioned. The air handler is usually placed away from the spaces that are air conditioned, in a different room. The air handler may get its air from outside or from the room, either through vents placed in doors or from ducts. The air handler may also be placed outside, contain a condenser and allowed to draw outside air. When these criteria are met, they are instead known as rooftop systems, rooftop units, rooftop packaged unit or packaged rooftop system.
A mini-split system typically supplies air conditioned and heated air to a single or a few rooms of a building. In these, the evaporator unit uses a cross-flow fan to blow air from the evaporator coil. The name mini-split is often used to refer to those mini-split systems that only supply air to a single room. Multi-zone systems are a common application of ductless systems and allow up to 8 rooms (zones) to be conditioned from a single outdoor unit. Multi-zone systems typically offer a variety of indoor unit styles including wall-mounted, ceiling-mounted, ceiling recessed, and horizontal ducted. Mini-split systems typically produce 9,000 to 36,000 BTU (9,500–38,000 kJ) per hour of cooling to a single room or indoor unit. The first mini-split systems were sold in 1954-1968 by Mitsubishi Electric and Toshiba, in Japan. Its invention was motivated by the small size of modern Japanese homes, and the large size of traditional ducted central split systems. Multi-zone (multi-split) systems provide extended cooling and heating capacity up to 60,000 BTU’s to multiple rooms or indoor units simultaneously. Large multi-zone systems are known as VRF (Variable refrigerant flow) systems, and are often used in commercial buildings. Multi-zone ductless systems were invented by Daikin in 1973 and VRF systems were also invented by Daikin in 1982. Both were first sold in Japan.
Advantages of the ductless system include smaller size and flexibility for zoning or heating and cooling individual rooms. The inside wall space required is significantly reduced. Also, the compressor and heat exchanger can be located farther away from the inside space, rather than merely on the other side of the same unit as in a PTAC or window air conditioner. Flexible exterior hoses lead from the outside unit to the interior one(s); these are often enclosed with metal to look like common drainpipes from the roof. In addition, ductless systems offer higher efficiency, reaching above 30 SEER.
The primary disadvantage of ductless air conditioners is their cost. Such systems cost about US$1,500 to US$2,000 per ton (12,000 BTU per hour) of cooling capacity. This is about 30% more than central systems (not including ductwork) and may cost more than twice as much as window units of similar capacity.”
An additional possible disadvantage is that the cost of installing mini splits can be higher than some systems. However, lower operating costs and rebates or other financial incentives—offered in some areas—can help offset the initial expense
Packaged HVAC Sytem
A Packaged Terminal Air Conditioner (often abbreviated PTAC) is a type of self-contained heating and air conditioning system commonly found in hotels, motels, senior housing facilities, hospitals, condominiums, apartment buildings, add-on rooms & sunrooms. Many are designed to go through a wall, having vents and heat sinks both inside and outside. Different standard dimensions are found in the market including 42×16 inches (1067 x 406 mm), 36x15 inches, and 40x15 inches.
Although PTACs are used mostly to heat or cool a single living space using only electricity (with resistive and/or heat pump heating), there are cooling-only PTACs with external heating through a hydronic heating coil or natural gas heating. Typical PTAC heating and cooling capacity values range from 2 to 5.5 kilowatts (7,000–19,000 BTU/h) nominal. One characteristic of PTACs is that condensate drain piping is not required because the condensate water extracted from the air by the evaporator coil is drawn by the condenser fan onto the condenser coil surface where it evaporates. Conventional PTACs still require condensate drain piping to be installed. The first practical semi-portable air conditioning unit was invented by engineers at Chrysler Motors and offered for sale starting in 1935.